|Material:||Cold Rolled Steel||Application:||Chemical Storage|
|Fire Rating:||2 Hours||Standard:||FM Standard, OSHA|
walkin explosion proof container,
ZOYET explosion proof container,
ibc explosion proof container
This product is suitable for storing drums and IBC large container; Apply in segregated storage of hazardous chemicals container, indoor or production workshop. Also use as outdoor container.
|W x D mm||7000 x 1800|
|Door Type||2 double door
Safely storing hazardous materials and wastes is a necessity for many companies.Outdoor Chemical Storage Buildings provide an effective solution to fulfill this need. The National Fire Protection Association (NFPA) defines an outdoor chemical storage building as "a prefabricated structure, manufactured primarily at a site other than the final location of the structure, and transported completely assembled or in a ready-to-assemble package to the final location." These buildings provide an economical means of storage and secondary containment because they eliminate the expense of constructing permanent structures. They also offer the additional benefit of being portable, allowing the buildings to be relocated should the need arise.
If the materials to be stored are either flammable or combustible, you will need a building that meets the NFPA Code 30, Uniform Fire Code (UFC) Articles 79 and 80, or an equivalent local code. Check with the authority having jurisdiction (AHJ) to determine which code is locally enforced.
The interior of the building should accommodate the number of containers required in a single layer and have adequate sump capacity to comply with the Environmental Protection Agency (EPA) Secondary Containment Requirements (40 CFR 264). To meet this regulation, the sump containment should be large enough to hold 100% of the volume of the largest container stored in the building or 10% of the total volume of all containers stored in the building, whichever is larger.
Q: Can outdoor chemical storage buildings be moved from one location to another?
A: Yes. Outdoor chemical storage buildings are designed to be portable. When moving a building to a new location, be sure to confirm that the new location meets all required local codes. A building can also be moved indoors if needed. Buildings for flammable liquid storage being relocated indoors should have a continuous ventilation system that is exhausted to the outdoors, a four-hour fire rating, a fire suppression system and explosion relief panels directed towards a safe exterior location. Also, in most cases when storage is indoors and a sprinkler system is installed, the containment sump is required to be large enough to hold 100% of the volume of the largest container stored or 10% of the combined total volume of all of the stored containers, whichever is larger, plus the additional volume of the water discharged by the sprinkler system in 20 minutes.
Contact Person: Jully
Outside systems: Fire extinguishing system, emergency medical system, access control system and anti leakage system
Inside systems: Fire fighting system, pressure relief system, temperature control system, lighting system, ventilation system and explosion proof control system
Technology: European advanced technology and italy manufacturing process
Customized sizes: Available